Four, Eight, Sixteen Zone Style B (Class B) Initiating Device Circuits (IDCs), All zones accept
two-wire smoke detectors and any normally-open contact devices.
Two Supervisory Input with DC12V output, ideal to connect security alarm devices.
Three General Alarm, Trouble and Supervisory, Form A Relay Output.
One, Two, Four Built-in Sound Output, Style Y (Class B) Notification Appliance (Signal) Circuits
(NACs), NACs may be programmed: Silenceable or Non-Silenceable.
3.0 amps of total system power. Resettable DC24V & Non-resettable DC24V Output.
Zone Input Short Circuit can be set to “Alarm” or “ Fault” mode.
RS485 Communication Port (optional).
Automatic/Manual mode can be programmed.
Disable/Enable control per Zone (IDC) can be programmed.
Disable/Enable Sound Output(NACs) can be programmed.
AC POWER: 220VAC, 50 Hz.
BATTERY: Sealed lead-acid batteries only. Maximum charging circuit: 27.6VDC @ 0.8 amp for
normal flat charge. Maximum battery charger capacity: 18AH battery.
NOTE: Two 10AH batteries can be housed in the cabinet. Larger batteries require a separate
Total DC24V system power: 3.0 amps.
Maximum current per NAC: 1.25 amps.
Maximum battery charging capability: 18 AH.
Resettable four-wire smoke detector power output.
Non-resettable power output.
Integral Form-A Alarm, Trouble and Supervisory relays, rated at: 2.0 amps @ 30 VDC
(resistive), 2.0 amps @ 30 VAC (resistive)